Other components: support structure: is the part of the team that supports the photovoltaic panel. Normally they are manufactured from anodized aluminum, several photovoltaic modules are placed in it. This structure must be grounded electrically, must withstand winds that occur in the area of installation, so your Foundation is must be suitable. Electrical connection and protection elements: the PV array is connected directly to a switch on off of the system, and this is connected to the pump controller, since the controller connects the solar pump, the sizing of the caliber of the cable duct that goes to the pump is important since for standard voltage drop must not be greater than 3%the cable should be the proper gauge submersible type, proper bonding with the submersible pump must use gaskets Thermo contractile to ensure tightness on the power line. Incorporates a system of protection against atmospheric discharges and Lands system, both in the electric part as the structure. Driver: There are drivers with Visual cues of the functioning of the system that can incorporate a storage tank level switch, this driver also allows you to add different energy sources to pump as they can be wind power or even a conventional electric generator to gasoline or diesel in this way may have a system hybrid pumping. Pipes: Water conduction pipes ranging from pump to the storage tank, diameters and materials of the pipe depends on the quantity of water pumped, travel distance, materials used tend to be PVC pipe, black hose i.d 80 or galvanized pipe.
Depending on the terrain where feed water tubing is recommended burying it by the least fifty centimeters to avoid possible leaks due to the deterioration of the material for sun exposure, damage to them by animals or transit of vehicles, etc. Storage tank: the storage tank is the place where the water is deposited until it is consumed. It is recommended to store enough water for the consumption of at least three days, in the case of any possible maintenance of the equipment. If there are several points of consumption we recommend placing the storage tank so that the gravity which is responsible for the distribution.